750 V 70 C PVC Insulation, Single Core (TIS 293-2541, Table 1) NAY THW-A AWV Cable
1.Standards The cable meets the standard requirements of GB12527-90 or Q/SL109-2002.
Number of cores
Nominal Cross-sectional Area
NAY THW-A AWV
3.Using properties 1) Rated voltage U0/U is 750V. 2) Maximum continuous operating temperature requirements: ——For PE and PVC, 75°C. ——For XLPE, 90°C. 3) Installation requirements: ——Laying temperature shall not be less than -20°C. ——Minimum bending radius: For that whose diameter is less than 25mm, shall be 4 times cable outer diameter. For that whose diameter is equal to or greater than 25mm, shall be 6 times cable outer diameter. ——It should be considered to keep a certain distance between cables and trees during installation. Touch, between cables and trees, is allowable only for short time during operation.